ASME A112.6.2 pdf download FRAMINGAFFIXED SUPPORTS FOR 0FF-THE-FLOOR WATER CLOSETS WTH . CONCEALED TANKS .
This Standard establishes minimum performance re-qutrements for framing-affixed supports for off-the-floorwater closets with concealed tanks. It is not intendedto iimit the use of other materials, fnishes, and designsthat equal or exceed the requirements of this Standard
1.2 Units of Measurement
Values are stated in U.S. Customary units and theInternational System of Units (SI). The U.S. Customaryunits shall be considered as the standard.
The following documents form a part of this Standardto the extent specified herein. The iatest issue shaliapply.
ASME Aii2.6.iM,Fioor-Affixed Suppurts for Off-theFloor Plumbing Fixturcs for Public UseASME A112.19.2M,Vitreous China Plumbing FixturcsPublisher: The American Society of Mechanical Engineers (ASME).Three Park Avenue,New York，NY10016-5990
ANSI/ASSE 1002.Water Closet Flush Tank Fill ValvePublishcr: American Society of Sanitary Enginccring(ASSE),28901 Clcmcns Road,Westlake,OII 44145
A number of special terms, which are specific tothe supports described by this Standard, are definedherein. For additional terms pertinent to support andcarrier nomenclaturesee ASME AII2.6.1M
carrier: a concealed support for an off-the-floorAxture.
combination water closef support and htfing: an as-sembly for supporting off-the-floor water closets. which includes both support- and waste-fitting componentsand a concealed fush tank. See Fig. 1.
firring(s): the sanitary waste-fitting component(s) of acombination water closer support and fitting.
ixrure bolrs: the bolts on which the fixrure is mountedand which connect directly to the carrier.
foot.a memnber of a carrier, designed to rest on thefloor in a concealed location to anchor and supportthe assembiy.
gasket, fixture. the scaling elemcnt bctween fixtureand fittings.
integral tank: a fush tank that is provided as anoption to thc support asscmbly for the purpose offlushing the wall-hung fxture, which is usually con-cealed behind the finished wall.
offthe-fcor fxture: any sanitary plumbing ixture,located adjacent to a wall (partition), which has novisible contact with the foor in front of the wall.
2 MATERIALS AND FINISHES
Materials and finishes used in supports and carricrassemblies shall conform to the material requirementsas cited in ASME A112.6.1M. Waste fttings shall beof cast iron, bronze, plastic,or other materials capableof withstanding the pressure testing in section 4.
Off-the-floor framing-affixed supports for water closets shal! consist of an integral tank, a supply pipe tothe water closet, a waste fitting from the water closet.and support assembly. The support assembly shall incor-porate as a minimum a support structure complete withfasteners to mount and connect the fixture, fitting, andpiping to carry the waste from the fixture into ‘thewastc linc, means to afhix the assembly to the structuralfloor or wall, and any necessary gaskets to connect